An error occurred while sending the contact message
Contact message has been sent successfully
FN verification test. Current time characteristic curve
This test is applied to check the protection by automatic magneto-thermal switches or automatic differential switches under abnormal operation conditions of the installation.
The test methodology is based on verifying the characteristic curve that the MTCB (Magneto-thermal Circuit Breaker ) and DAS (Differential Automatic Switches ) are configured with from the factory, and which includes the following actions:
Thermal zone curve (Joule effect) on which circuit protection against overloads is based, since excessive current for a certain length of time produces a thermal gradient that affects a bimetallic strip fitted in the switch. When the gradient exceeds a set value for a given time, this strip causes the switch to open.
Thermal zone curve (Ampère’s Law) on which protection of the installation against short-circuits is based, defined by very high currents in respect of the dimension of the installation for a short period of time. In this case the actuator is an electro-magnet.
To perform the test, a series of currents at magnitudes that simulate and overload or short-circuit are injected into the tested device so that the time the circuit takes to open can be measured (trip time).
Este sitio web utiliza cookies para que usted tenga la mejor experiencia de usuario. Si continúa navegando está dando su consentimiento para la aceptación de las mencionadas cookies y la aceptación de nuestra política de cookies, pinche el enlace para mayor información.